Copyright Leonard's Air and Energy. All rights reserved.
This bag of flex was left connected to the main duct but not run into the sales floor. A small oversight that could have been a huge energy loss.
Cracked and worn fan belt, also the motor bracket was cracked. This building was paying a maintenance contract, they have since switched companies.
Outside air fan filter completely loaded causing humidity issues in the building.
Leonard's Air and Energy Service
Independent Test and Balance